About Emergency box
Fagerhult's emergency lighting for Pleiad contains both electronic parts and batteries (NiMH). The batteries have 1 or 3 hours operating time. The box is available in three different styles: A standard version without self-test, a potential free version with self-test and a DALI version with self-test. The self-test is in accordance with EN 62034. The boxes are intended to be recessed in unventilated or ventilated ceilings. The diode that indicates the charge/status is connected to the luminaire. The battery has its own space on the side of the box; protecting all heavy current components against unintentional when changing the batteries. The boxes are designed in class II, IP 20 and are F marked.
The box is supplied with a 15-way multi connector installed on 0.25 m wiring, for simple connection to the intended luminaire. All external connections are made in a separate space in the emergency box. The boxes are prepared for the connection of control cables that allow for dimming. The terminal block is equipped with integrated fuses for incoming phases (ignition and charging phases). If there is a fault in the emergency lighting luminaire, or faulty work in the installation, the fuses create greater safety. Boxes with self-test are also equipped with separate terminal blocks for connecting DALI or supervision systems based on the use of potential free contacts.
The emergency boxes require specially prepared luminaires with HF-standard or HF-dim, which are supplied with diodes for charging/status and equipped with the corresponding multi connector as the box. The box can be combined with luminaires with 13–57 W FSQ-E/ FSM-E light sources. We recommend mercury type light sources, but amalgam light sources may also be used.
Downloads Emergency box
Marking of product sheet
Functions Emergency box
Accessories Emergency box
Replacement battery emergencybox
|Replacement battery emergencybox 98014-16||98028|
|Replacement battery emergencybox 98017-19||98029|